Alert: Notifications at reduced capacity during COVID-19 restrictions
We are operating at reduced capacity due to the COVID 19 alert level four requirements.
Please only call our 0800 number if someone is at serious risk of harm or has been seriously injured, become seriously ill, or died as a result of work.
For other notifications please complete our online forms at Notify WorkSafe.
There are three levels of risk classification for gasfitting. These are low-risk, high-risk and general. There are more requirements for certification for high-risk and general gasfitting than there are for low-risk gasfitting.
Regulation 5A defines the three categories of gasfitting work as low-risk, high-risk, and general. This categorisation focuses resources and attention where they are more likely to be needed to achieve compliance and safety.
The risk-based approach to certification means that there are fewer requirements for low-risk gasfitting than there are for general or high-risk gasfitting.
Low-risk gasfitting is any of the following:
- Replacement of a gas appliance with an equivalent gas appliance, except in a caravan or boat with sleeping quarters, provided the work does not involve:
- the repositioning of pipework or flue, or
- a change in the installation pressure, gas type, ventilation, energy consumption, or operation of the installation.
This is sometimes referred to as ‘like for like’ gasfitting
- The maintenance of fittings and appliances other than repairs following a notifiable accident
- The replacement of instrumentation and related controls, but only if the work does not result in the repositioning or disturbance of other pipework
- The setting of safety devices, combustion conditions, and controls that are not designed to be adjusted by a consumer or gas refueller
- Temporary gasfitting for experimental, testing, demonstration, teaching, or research purposes in a gas engineering workshop, manufacturing facility, gas test facility, laboratory, hospital, research project, or teaching institution.
- Gasfiting for the purposes of testing in accordance with NZS 5255 or NZS 5266.
High-risk gasfitting is work which is not low-risk gasfitting and meets one or more of the high-risk criteria. Specifically, high-risk gasfitting is any of the following (provided it is not already assessed as low-risk):
- Addition or alteration to an existing installation
- Work not carried out in accordance with the means of compliance in applicable AS/NZS 5601standard
- Work on an installation that includes gas pressure-raising equipment
- Repair work following a notifiable accident
- Work in domestic premises where the maximum operating pressure is more than 7 kPa for natural gas or more than 14 kPa for LPG
- Work in a building of more than three storeys which contains three or more separate dwellings
- Work done to AS/NZS 5601.1 where the supply pressure to the installation is greater than 200 kPa
- Work done to AS/NZS 5601.2 where the supply pressure to the installation is greater than 3 kPa
- Work done within 20 metres of a hazardous area
- Work done in a building in which air pressure is controlled by a mechanical ventilation system
- Work done in a place where combustion air may be varied by mechanical means
- Work done in a caravan or boat that contains sleeping accommodation.
General gasfitting is gasfitting that is not categorised as low-risk or high-risk work.
Example of gasfitting risk classification
To see how these risk categories are applied here is an example using a gas hob connected to a 9 kg cylinder, working through the risk criteria in the order they should be applied:
- If the gasfitting work is replacement of the appliance that does not require repositioning of pipework or a change in the installation pressure, gas type, ventilation, energy consumption, or operation, and provided it is not in a caravan or boat with sleeping quarters, it is low-risk gasfitting
- If the gas hob is installed in a caravan or boat with sleeping quarters it is high-risk gasfitting
- If the gas hob is installed as part of an addition or alteration to an existing installation it is high-risk gasfitting
- If it is a new installation of a gas hob, it is general gasfitting.